Metallic Piping to be Bonded continuously with a #8 copper bonding wire and bonding clamps, to cold, hot, and lines to tie systems together at water heater. Water Heater Stand or built in platform is required when water heater is installed in a garage to elevate water heater a
Bonding 7 Water Chemistry Maintenance 8 Heat Pump Features 9 Heat Pump Operation 10 Control On/Off 10 control box of the heater for the bond wire to be attached. Warranty will be void if system is not properly bonded. Attach Bond Wire From Pool Pump Here
Conductor in a 240volt circuit (such as the circuit for an electric clothes dryer, electric water heater, or The main bonding jumper can be a wire, screw, terminal bus, or other suitable conductor. Main Panel Main Bonding Jumper
Water connections are made at the rear of the heater. Both water in and out are labeled just above the water pool pump bonding terminal or other suitable location. NOTE: Loose sensor wire Defective water thermistor HC Water Thermistor
RESIDENTIAL GAS WATER HEATER Bonding Bond hot and cold water lines and gas line with #6 copper wire and approved clamps. Tank less water heaters shall be listed by an approved testing agency (UL, UPC, etc.) and be installed in accordance
Bonding a) All metal piping systems to be bonded . b) Jumper from cold water to hot water piping typical at water heater . c) Bond wire sized the same as the required GEC, minimum #8 gage . 5. Meter/Panel a) Height 66" maximum, 48" minimum .
8AWG Bonding Wire (Included with your heater – *May Be on Bottom of Tube*) To Bathtub Bonding System BONDING YOUR HEATER Wwww.bathheaters.com Bonding Lug Replace Heater WATER LEAKS FROM CONTROL BOX Defective Component – Replace Heater GFCI TRIPS OCCASIONALLY
Water heater installations in bedrooms and bathrooms shall comply with the provisions bonding wires and then grounded to prevent shock hazards should an energized electrical wire come in contact with the pipe.
This shall consist of 20’ of ½” bare or zinc-coated rebar or bare copper wire in the portion of the footing in contact with earth. Bonding shall consist of a continuous bond jumper installed at the water heater between the hot,
680.8 Overhead wire clearance is min. 10’ horizontal from the pool wall. Bonding to a pool water heater. 2. Installing a metal pipe nipple in the water circulation system so a ground strap may be attached to it. 3. Other approved methods.
water heater. This brochure covers the BONDING Metallic water and gas pipes shall be #8 or larger copper wire is required for bonding the gas, hot and cold water piping at the water heater. INSPECTIONS Usually only one inspection is needed
Filled with hot water, With a No. 8 solid copper wire, bond the heater to bonding lug has been provided on the heater. At initial start-up and before each use thereafter with power ON, push the GFCI test button. The reset button should pop out.
11. Protection: If the water heater is located in the path of travel of a vehicle a method of provid-ing protection is needed. A 4” pipe filled with Use bonding wire that is the same size as grounding conductor for electrical service and bond-ing clamps.
Generally the replacement of a water heater does not affect the bonding of the pipes. It is recommended that a #8 copper wire be connected to the gas, hot water, and cold water pipes using clamps that can be obtained at a hardware store.
Are replacing an existing electrical water heater of the same size. BONDING It is recommended that a #8 copper wire be connected to the gas, hot water, and cold water pipes using clamps that can be obtained at a hardware store. RAISED PLATFORMS
Junction box is for bonding the heater to a grounded service entrance conductor, a grounded service entrance raceway, or an earth grounding electrode conductor. wiring for 3 wire lead water heaters *note: if a 2 wire circuit is required, connect the red