Water Heater Troubleshooting Verify igniter is working. Turn off gas valve feeding the appliance. Unplug igniter wire; hold the igniter wire with
And when the igniter and burner are operating. This water heater design has been tested by CSA International and complies with ANSI Z21.10.1, ABS, or CPVC pipe. Water heater(s) shall have combined vent capabilities of up to 120’ to
STEP 9 – IGNITER RESISTANCE TEST Unplug water heater power cord from wall outlet, turn the on/off switch to the “off” position. Disconnect the 4 pin igniter plug from the “C2” receptacle on the SmartValve.
95% Efficient 1. The quiet, brushless DC blower prepurges the submerged combustion chamber for 8 seconds and turns off. 2. The hot surface igniter is energized and glows
© 2012 Reliance® Water Heater Company RPGPCR0112 FIRST HOUR RATING 68 Gallons INPUT 35,500 BTU RECOVERY (Gallons/Hour) 36 Gallons Piezo igniter allows for easy “one-hand” pilot ignition without matches Factory-installed PEX polymer lined nipples
A.O. Smith Water Heater Parts Fulfillment 125 Southeast Parkway • Franklin, TN 37068 www.hotwater.com • 1-800-433-2525 Igniter .. 9006101205 ..9006101205 13. Intake Connector ..197604-000
PRINTED IN THE U.S.A. 0606 185480-001 MODELS: 8 40, 50 YAVIT/HAVIT 6 40, 50 YBVIT/HBVIT Series 100, 101 Reliance Water Heater Parts Fulfillment • phone: 1-800-821-2017 • www.reliancewaterheaters.com
Gas Water Heater with the Flame Lock™ Safety System Installation Instructions and This will not prevent a possible fire/explosion if the igniter is depressed and flammable vapors have accumulated in the combustion chamber with the pilot light off.
Matches or grill igniter Step One Drain the Tank 1. Turn off the water and gas supply. 2. Attach a garden hose to the drain valve and empty Install the water heater in an area with at least six inches of clearance around it for ventilation.
Ladder diagram – water heater models 150,000 – 300,000 btu / hr thermostat r1 w1 transformer igniter ign mod p5 air blower combustion a off on power switch l1 (hot) l2 to 120 vac power supply 24 vac 120 vac lwco lwco 6 2 lbl20019 rev a * if equipped pump delay 24vdc
Flammable Vapor Ignition Resistant Water Heater Troubleshooting Guide present the igniter is not functioning and must be replaced. Step 4. With orange wire disconnected from Piezo igniter. Using a common screw driver, place blade of screw
water heater is exposed to freezing temperatures, the water in the coils could freeze, causing a break in the heat exchanger of the unit, or the supply and return lines. This kind of damage will result in water running freely into the space where the water heater is located,
When the power is on and when the igniter and burner are operating. This water heater design has been tested by CSA International and complies with ANSI Z21.10.1, Water heater(s) shall have combined vent capabilities of up to 120’ to the
Ignited by a gas water heater’s hot surface igniter or main burner. The resulting flashback and fire can cause death or serious burns to anyone in the area. This heater is equipped with a FV sensor for detecting the presence of flammable vapors.
water heater. Piezo Igniter Residential Direct Vent Water Heater NATUR AL GAS AND LIQUID PROPANE GAS Direct Vent Energy Saver Models Meet or exceed ASHRAE 90.1b (current standard) C.E.C. Listed 79% Recove ry Ef®ciency Model Number
Igniter Load: 5A maximum at 120 Vac. Induced Draft Motor Load: 2.5A Full Load, 10A Locked Rotor at 120 Vac. Current: 0.100A at 115 Vac water heater control application, but the specific controls used and the procedures outlined by
© 2012 Reliance® Water Heater Company RPGPCR0112 FIRST HOUR RATING 90 Gallons INPUT 50,000 BTU RECOVERY (Gallons/Hour) 51 Gallons Piezo igniter allows for easy “one-hand” pilot ignition without matches Factory-installed PEX polymer lined nipples
PIEZO IGNITER, ELECTRODE TESTING AND REPLACEMENT With the pilot not in operation (no pilot flame) you can check the Piezo and electrode circuit by viewing pilot